67 Lombard Street
Building Name: 67 Lombard Street
Customer: Cushman & Wakefield
Size: 10,452 m²
Location: 67 Lombard Street
Summary: Jaguar’s Technical Team attended 67 Lombard Street to carry out scheduled Thermal Imaging. It was noted the Power Factor Correction Unit was in fault and out of use, our team were advised the unit needed replacing. Upon closer inspection, using a voltage indicator it was found that one of the PFC voltage reference connections had failed. The unit was safely isolated, voltage reference connections remade, and PFC reinstated free from any faults.